Weight of the unit, kg 0,15 + 0,02 Weight of aerosol-forming charge, kg 0,03 ± 0,003 Fire control capability, kg/m³ 0,05 Maximal protected volume of the nominally tight room (δ* < 0,001m-1), m³ 0,6 Dimensions, mm (diameter х height) 75 х 28 Operating time, sec 8 + 0,8 Classes of fire fighting
By applying an electrical or thermal pulse to the activation unit the aerosol-forming block ignites, the combustion of which forms gas-aerosol fire-extinguishing mixture consisting of fine particulates (potassium salts being potent inhibitors) about 70% of the original weight of the composition and the gas phase, which enters the protected volume.
Standalone aerosol fire extinguishing unit with a thermal starter AGS 12/2 shall be installed on the enclosing structures.
Fastening is carried out using different types of hardware through 3mm diameter holes or double sided tape.
Before tape fastening, you must degrease the surface for the installation of the product. Remove the protective film from the back of the unit AGS 12/1. Press firmly to the surface. Fastening is possible using hardware
Installation by tape should be in a heated room, under normal climatic conditions, then a temperature mode should not be changed for 3 hours.
Download, PDF (150 Kb)
Standalone aerosol fire extinguishing unit with a thermal starter AGS 12/2
Standalone aerosol fire extinguishing unit with a thermal starter AGS 12/1 is a saturation extinguisher and intended to control and extinguish fires of flammable and combustible liquids, solid fuels and electrical equipment, including energized one.